DETAILED DESCRIPTION & SPECIFICATIONS
Being a vertical unit, there will always be space for the TT BOILERS Steam Buffer - and it works with any brand of steam generator
Nice to have OR Need to have
Even though the unit and
the installation is quite economical and it only takes about half a
square meter on the floor, it is not always the situation that you must
have TT BOILERS Steam Buffer.
STEAM DRYER (SEPARATOR)
In continuation of this problem, AB&CO have developed the TT BOILER Steam Buffer - a special unit that offers some unique features not only eliminating the above problem, but also gives extra advantages to the steam generator compare to the classic fire tube boiler.
The unique thermodynamic design makes it possible to accumulate steam capacity to withstand short peak loads in the steam consumption, using a reservoir of feed water maintained at boiling point just like the classic fire tube boilers. While developing an efficient steam buffer, AB&CO took a large step further and extended the features on the unit.
Consequently TT BOILERS Steam Buffer is now probably the best steam dryer on the market, where even quite wet steam becomes 98-99& dry saturated steam.
TT BOILERS steam Buffer also offers the possibility to adapt the burner (heat input) any loads. With this the steam generator can be supplied with a modulating (step-less) burner. The steam generator will no longer be sensitive to the adjustment of water in the steam. In the TT BOILERS Steam Buffer the water will be separated off and accumulated for future peak load. Any excess of water here will be drained-off and led back to the condensate tank in a cooled condition. Normally it is very difficult to adjust the feed water amount to the burner in all operational conditions especially start-up and shut-down, but it is nevertheless required when you do not have a unit installed like TT BOILERS Steam Buffer.
Finally the TT BOILERS Steam Buffer are designed so that any condensate / feed water leaving the unit is cooled down - which contribute efficiently to elimination of risk for cavitation of feed water pump and steam present in the the boiler room.
There are no
sophisticated armatures, instrumentation and electronics. Nothing that
requires careful adjustment and re-adjustments, nothing that can break
down It simply utilize laws of nature presented in the well-known rigid TT